View and Download YOKOGAWA EJXA installation manual online. EJX Series and EJA-E Series Differential Pressure and Pressure Transmitters. EJXA. Manual. Yokogawa Electric Corporation. EJX Series. HART Communication Type .. This manual describes the HART protocol communica- 1 EJXA Get Yokogawa EJXA Manual. Get all Yokogawa manuals!.
|Published (Last):||3 August 2010|
|PDF File Size:||10.85 Mb|
|ePub File Size:||20.68 Mb|
|Price:||Free* [*Free Regsitration Required]|
Never piping and connecting the impulse piping to a transmitter. Zero adjustment Conduit connection 54 2. This manual also for: By pressing ‘print’ button you will print only current page.
YOKOGAWA EJX110A Installation Manual
The mating flange, gasket, stud bolts and nuts are to The FEP Teflon option includes a teflon film and procured by the customer. A failure to abide by these restrictions could Page 17 Note 4.
Refer to the installation diagram Non-Hazardous Location Note 4. Location of ejx110w mark requirements of each system. It can be fixed at any angle within above range. Selecting the Installation Location NOTE Ground terminals are located on the inside and outside of the terminal box. Maximum Internal Capacitance Ci: However, to ensure that it will provide years of stable and accurate performance, take the following precautions when selecting the installation location.
Comments to this Manuals Your Name. Ex d IIC T The air must be removed to ensure Gasket Power Supply Voltage and Load Resistance This instrument has been tested and certified as being intrinsically safe or explosionproof. Since this will cause errors mwnual the measurement output, select the proper piping method covered with a plastic cap to keep out dust.
Yokogawa EJXA : Manual
This cap must be removed before connecting the piping. Tell us what’s missing. Maintenance of the transmitter is easy due to its modular construction. Diaphragm sealed differential pressure transmitters 76 pages. Refer to General Specification for maximum working pressure of a transmitter.
Don’t have an account? Do not install the transmitter in a corrosive atmosphere. Occasionally, however, temporary conductivity caused by condensation must be expected. Flange mounted differential pressure transmitters 54 pages.
NO Are valves opened or closed correctly? Page 11 b Manuaal apply a voltage exceeding V DC V DC with an internal lightning protector for the insulation resistance test, nor a voltage exceeding V AC V AC with an internal lightning protector for the dielectric strength test.
Never insert a Drain valve screwdriver or other tool between the cap and port threads to remove the cap. Changing the Direction of Integral Indicator To reposition a drain vent plug, use a wrench to slowly and gently unscrew it.
What’s missing? Tell us about it.
Screw each cover in tightly until it will not turn further. Page 55 Revision Information: Page 85 ii Edition 7th 8th Date Feb.
Add HART 7 manual. Please read it along with the standard manuals.